Step-by-step design advice
in 30 short video segments
Our complete Natatorium
Design Guide in PDF format
A helpful 9-point natatorium
The designer should address the following issues to ensure the unit is properly installed and can be serviced and maintained.
No Access = No Service or Maintenance. All NE series dehumidifiers have been designed to require access on only two sides. Allow a minimum of 36 inches of clearance on the sides indicated for piping and service access. Mirror access units are also available.
Seresco has developed the simplest and most reliable water heating configuration in the industry. NE Series dehumidifiers can be equipped with water heating capabilities. The annual energy savings realized as a result of the water heating capabilities makes this unit configuration one of the most energy efficient units in all of the HVAC industry.
The NE unit requires only a fraction of the total water being circulated by the main filter system.
This heat exchanger is used in air conditioning mode where it rejects unneeded heat from the space to outdoors. Proper installation is essential to ensure it can function as intended. Proper airflow and refrigerant piping are paramount.
The NE Series dehumidifiers have all necessary sensors unit mounted and set points pre-programmed at the factory. Remote duct heaters, outdoor air-cooled condensers, auxiliary pool water heaters and remote exhaust fans all require interfacing with the dehumidifier. The microprocessor has been programmed to control their operation. An Ethernet connection to the Internet allows all functions to be monitored by trained professionals with Seresco's WebSentry. It is the final step to ensure the facility operates trouble free.
Unit mounted sensors, all accessible via the Internet include: